01 of 05
The electronic ignition system in a gas furnace is a modern development that provides more reliable performance than a standing pilot and offers energy savings through better furnace efficiency. There are two basic types of electronic ignition systems:
- An intermittent pilot system uses an electronically controlled high-voltage electrical spark to ignite a pilot light and subsequently the main burners when the thermostat calls for heat.
- A hot surface ignition system uses an electronically... controlled resistance heating element, not unlike a light bulb filament, to ignite the gas burner.
Understanding some of the basic components of a modern furnace will help you identify the type of furnace you have and narrow down the list of potential problems. Here's a quick overview of furnace designs and components found in high-efficiency furnaces using electronic ignition.Continue to 2 of 5 below.
02 of 05
Types of Electronic Ignition Furnaces
Most furnaces with electronic ignition are either conventional induced draft furnaces or high-efficiency condensing furnaces.
Induced draft furnaces use either an intermittent pilot (IP) or hot surface ignition (HSI) instead of a standing pilot light. Also, unlike a conventional furnace that creates a natural draft by drawing in air from an opening in the front of the furnace, an induced draft furnace uses a small fan to draw the combustion gasses into the flue. The combination of electronic... ignition, electronic controls, and artificially created draft improves the efficiency of induced draft furnaces over older conventional models.
Condensing furnaces use two heat exchangers, where conventional furnaces use only one. After the gas is burned to heat the primary heat exchanger, the secondary heat exchanger draws heat out of the hot exhaust gasses, cooling them to the point that the water vapor in the exhaust condenses into water. The resulting flue gases are so cool they can be vented outside via a plastic (PVC) pipe, while the condensed water is run to a floor drain. Condensing furnaces use hot surface ignition.Continue to 3 of 5 below.
03 of 05
Troubleshooting an Intermittent Pilot (IP)
Typically found in induced draft furnaces, an intermittent pilot ignites the burner gas with a high-voltage spark only when the thermostat calls for heat. Once the pilot is lit, and the main burner senses the pilot flame (using a flame sensing rod), the main burner ignites. The intermittent pilot flame goes out after the heating cycle and remains off until the next time the thermostat calls for heat.
The furnace gas valve for this type of furnace is identifiable with its solenoid designations:... MV, PV, and PV/MV — where MV = main valve, PV = pilot valve, and PV/MV = common.
Common problems with IP ignition include:
Continue to 4 of 5 below.
- Ignition doesn't, and the furnace won't go on
- A spark is present, but the pilot won't light
- Pilot lights, but the main burner doesn't come on
- Burners ignite but turn off after a few seconds
04 of 05
Troubleshooting a Hot Surface Igniter ( HSI)
The hot surface igniter (HSI) is the most commonly used electronic ignition system. It works like a light bulb filament, heating up when electricity is passed through it. Most are made from silicon nitride or silicon carbide. The igniter is located in the flow of gas entering the burners.
When the thermostat calls for heat, 24 volts are sent to the electronic ignition control module, which energizes the furnace blower and other systems and sends 120 volts to the HSI. The HSI heats up to around... 1,800°F to 2,500°F and glows red-hot. Then the gas valve opens, and the burner gas is ignited by the HSI. Once a proper flame is sensed by the flame sensor, the HSI turns off and stays off until the next heating cycle. In some furnaces, the HSI also serves as a flame sensor (called local sensing) instead of having a separate sensing rod in the burner flame (remote sensing).
Under normal conditions, an HSI should last for 3–5 years, and they eventually crack and need to be replaced. This can happen sooner if the oils from your skin get on the element through improper handling. That means: Don't touch the element with your bare hands!
HSIs usually cost between $25 and $50, and it's a good idea to keep a spare on hand, in case one goes out at night or on the weekend, when you can't easily get a new part.
Here are some of the common causes of HSI failure:
Continue to 5 of 5 below.
- Premature failure due to improper handling (oil from skin got onto element)
- Improper igniter
- End of normal usage life cycle (keep a replacement on hand)
- Electric current in the home is too high (over 125 VAC)
- Severely dirty air filter, causing the high-temperature limit switch to cycle the furnace ignition on and off frequently
05 of 05
Reading Control Board Codes
Most modern furnaces with electronic ignition systems have an integrated circuit board that controls many sophisticated processes. The boards can perform self-diagnostics and provide failure codes, similar to the diagnostic computer in your car.
If a failure occurs, LED lights on the control board light up in a blinking pattern to indicate a specific failure code. The codes are listed in a chart in the owner's manual and usually on a door or access panel on the furnace. Control boards are... usually located inside the blower compartment of the furnace. If the board has blinking lights, refer to the chart to decipher the code and help identify the problem area with the furnace.